This thread has been locked.
If you have a related question, please click the "Ask a related question" button in the top right corner. The newly created question will be automatically linked to this question.
CCS/MSP430F5324: Modbus Baudrate
Part Number: MSP430FR2155
Tool/software: Code Composer Studio
I am working on MSP430FR2155 microcontroller, In that I am using MODBUS RTU. In my controller I am using Uart to communicate with MODBUS, but in that I am not getting proper responses. I am checking the result on Modscan32, Valid slave responses are lesser then Number of Polls. How can I overcome this problem, Please suggest?
MODBUS RTU is Application Layer Protocol based on UART
On the usage of UART on MSP430FR2155 microcontroller, please refer to the code example of FR2155: www.ti.com/.../slac740
On MODBUS implement on MSP430, please refer to the previous E2E discussion: https://e2e.ti.com/support/microcontrollers/msp430/f/166/t/191447?Modbus-MSP430-communication-strange-response
We are glad that we were able to resolve this issue, and will now proceed to close this thread.
If you have further questions related to this thread, you may click "Ask a related question" below. The newly created question will be automatically linked to this question.
Could you provide some details about this issue? some hardware connection and Partial related code.
It may be better if you have some test data.
Search E2E! Your questions may already be answered!
If my reply answers your question please click on the green button "This resolved my issue".
Useful pages: TI Cloud Tools MSP Product Page
I haven’t heard from you for ten days, so I’m assuming you were able to resolve your issue. If this isn’t the case, please click the "This did NOT resolve my issue" button and reply to this thread with more information. If this thread locks, please click the "Ask a related question" button and in the new thread describe the current status of your issue and any additional details you may have to assist us in helping to solve your issues.
In reply to Johnson He:
Thanks for reply,
Actually I am working on 2 timer interruts. One is used for MODBUS with ACLK clock and 400 timercount and other on 8MHZ with 5000 count. So I am not getting is there any clash happening in it or any other reason in between these two timers. please help.
In reply to Sandhya Yadav:
Do you suspect that the 8MHz Timer interrupt conflicts with the ACLK interrupt, causing no proper responses in the MODBUD message?
You can turn off the 8MHz timer interrupt and test again.
All content and materials on this site are provided "as is". TI and its respective suppliers and providers of content make no representations about the suitability of these materials for any purpose and disclaim all warranties and conditions with regard to these materials, including but not limited to all implied warranties and conditions of merchantability, fitness for a particular purpose, title and non-infringement of any third party intellectual property right. No license, either express or implied, by estoppel or otherwise, is granted by TI. Use of the information on this site may require a license from a third party, or a license from TI.
TI is a global semiconductor design and manufacturing company. Innovate with 100,000+ analog ICs andembedded processors, along with software, tools and the industry’s largest sales/support staff.